SETTING UP YOUR C1D1 EXTRACTION BOOTH
HAL Extraction Booth Systems are shipped for easy on-site construction. You will need a forklift to unload the crate upon delivery. The largest panels measure 40″ x 120″ x 3″. If you can get that panel into your space, you should be able to set up an Extraction Booth System.
A crew of two or three can assemble a small Extraction Booth in 12-16 hours, ready for connection to mechanical and electrical systems. There is no need for large overhead freight doors or demolition to get the system in place. Assembly time may vary based on the size unit purchased.
All HAL Extraction Booths are powered by a 208VAC 1PH circuit.
The Class I, Division 1 Extraction Booth must be assembled a minimum of 3 ft from all walls, unless those walls have a 1-hour fire-rating.
All exhaust ducting must be vented outside. Supply air can be ducted from outside, or the surrounding space, as long as the space can provide adequate air-flow. The exhaust cannot be recycled back into the supply side ventilation.
CLASS I, DIVISION 1 EXTRACTION BOOTH PLACEMENT
The Extraction Booth System is assembled from the exterior, so space for the worker is required between the exterior wall of the Extraction Booth System and walls of the building.
The Extraction Booth shall be installed a minimum distance of 3 feet from all operations. The Extraction Booth can be installed within 3 feet from all operations if it is separated by a partition, wall, or floor/ceiling assembly with a minimum fire resistance a 1-hr as defined in NFPA 33 (2018) 5.5. Multiple connected booths shall not be considered other operations. One or two of the walls of the extraction room structure may be moved into place against a wall of the building provided the building wall carries a fire rating of one hour or greater.
The control panel may be placed on any 40” booth panel located at least 3 feet from the entry door or Utility Penetration Plate. The space within 3 feet of the entry door opening, and the Utility Penetration Plate, is a Class I, Division 2 hazardous location. Only electrical equipment rated for Class I, Division 2 locations can be located within this barrier.
The Extraction Booth is designed for indoor use only. The components are not designed for exposure to weather.
SHIPPING AND RECEIPT
The Extraction Booth structure and fan is shipped in one or two crates, depending on the Model.
A forklift is required for unloading of the crate(s) at delivery. HAL Extraction can also coordinate Call-Before-Delivery service along with your freight delivery.
EXTRACTION BOOTH MODELS
The HAL Extraction Booth is a turn-key Modular CI/D1 Extraction Solution for hydrocarbon and Class IB flammable solvents.
Our patent pending technology has been designed to provide the easiest and safest solution for extraction using flammable solvents.